600adjustable Air Differential Pressure Switch - Chinaprice: contact company for price
Please check if the switch body is leaking. If so, it is damaged and cannot be installed. The switch body should be installed on a vertical stable flat. And it should be near the pressure connection site as much as possible. It will decrease the distance for pressure connection and improve the performance.
1. Installing position:
Vertically installed and P1 & P2 downward as Fig. 1 is the best way. It can eliminate the possible condensing, and it is the factory-calibrating position.
- Can be installed horizontally when the environment does not have any condensing. On this way, Fig. 2 is recommended. The cover is upward and the switch value should plus about 20pa.
- When it can only be installed as Fig. 3 (does not recommend this way), the switch value should minus about 10pa.
2. Fasten with screws:
For the product with ear installation, fasten the 3 screws (max. φ4mm) directly into the ear on the installation flat. Do not fasten the screws too much. Otherwise, the switch could be damaged.
For the product without installing ear, it must be installed with the “U” shape bracket. This bracket is standard accessory and was connected with the switch body in factory. Simply fasten the 3 screws (max. φ5.4mm) into any 3 holes of the bracket on the installation flat.
Do not let the pipe to be tied as a knot, especially when the pipe passes edges and corners. Otherwise, the switch cannot work.
1. Insert the 2 pressure connection parts as Fig. 4 with the long side (60mm) into the prepared holes. Each part should be installed with 2 screws. Be sure to airproof the holes after installing.
2. Connect the plastic pipe. The standard accessory is 2m long with inner φ6mm. Cut the pipe as short as possible to connect the ports P1 & P2 on the switch and the short side of Fig. 4 parts. P1 is high port on the bottom of the switch and P2 is low port on the switch body as Fig. 5.
-After connecting the pipe, please check if the connecting is tight. And it should be inspected on daily maintenance. The switch cannot work if it is leaking.
600Adjustable Air Differential Pressure Switch
The operating technician should be trained and operate regularly.
Be sure to DISCONNECT the external power before electrical wiring. Otherwise, possible damage or even electric shock could happen.
1． The switch body as Fig. 6 is under the plastic cover.
And the contact principle is:
2 Normal Close Contact
3 Normal Open Contact
2．Pressure/Differential Pressure setting
The field adjustable scale indicates the set point. It means the contact will actuate when the applied (differential) pressure increases to it. This scale is accurate only when the switch is installed vertically with the P1 and P2 ports download as Fig. 1. When the applied (differential) pressure falls down below the set point, the contact will restore to the original status.
-open the upper cover.
-screw the printed scale dial ( A in Fig. 6) to required set point. It should be operated with a “一” shape screw driver.
-wire the screw terminals 1, 2 or 3 as required.
-restore the cover closely.
Be sure to start testing after the upper cover is closed. Use instruments if needed. Increase the applied (differential) pressure slowly. When it arrives the set point, the contact actuates. Then decrease the (differential) pressure slowly. When it is lower than the set point, the contact will restore to the original status. Please note the dead band characteristics for this product. If the actuations are correct, the installation and all pressure/electrical connections are finished correctly.
The max. working differential pressure is 7500Pa. If over pressured, the switch will be damaged.
- Posted By: Beijing Jamedoorla Technology Co.,Ltd
- Phone: 13120322487
- Address: Yang Ming Square,10 Xiao Ying Rd.,Chao Yang Distri, Beijing, China
- Website: http://www.lighthouse-china.com
Published date: July 11, 2013 -
- Business Description: Beijing Jamedoorla Technology Co.,Ltd., founded in 2001, is a
professional instrument supplier. Companies adhering to the world
advanced technology level, it is Shared with clients continuously
strengthen cooperation with foreign well known manufacturers, imported
high quality instruments and recommend to the user. As the world's many
famous instrument manufacturers in China agent (American DWYER, ARTI
KANOMAX Japan plus field, RION) companies to provide relevant measure
pressure, temperature and humidity, wind speed, noise, and other indoor
environment testing instruments products. Widely used in hvac, clean
room clean, biotechnology, electronic semiconductor chip industry, food,
pharmaceutical, aerospace and other fields.
Lighthouse3016handheld Dust Particle CounterAudio Electronics - Beijing Jamedoorla Technology Co.,Ltd - China - July 11, 2013 - contact company for price
Economical design and lightweight appearance, Wright hao series handheld particle counters in the market have handheld particle counters The advantage of high 6 channel synchronization of particle counting, Wright hao, handheld particle counters, thr...
Lighthouse3350 5350 Portable Laser Particle Dust CounterAudio Electronics - Beijing Jamedoorla Technology Co.,Ltd - China - July 11, 2013 - contact company for price
Fast sampling per cubic meter of 10 minutes, with 0.3 mm and 0.5 mm induction of cubic feet per minute 1 and 2 cubic feet per minute compared to counter Solair3350 and Solair5350 portable air particle counter can provide faster clean room identificat...
Dwyer Ir1 Subminiature Infrared ThermometerAudio Electronics - Beijing Jamedoorla Technology Co.,Ltd - China - July 11, 2013 - contact company for price
Subminiature temperature measurement, infrared thermometer allows for process does not apply to the traditional contact measurement. PIR1 through the use of the button will real-time display the maximum temperature, minimum value, average error or re...
Safe Trade Tips
- Ask for business references and check them
- Verify their business via their local Chamber of Commerce